If you’re looking for help fixing your McQuay furnace, look no further! Our comprehensive McQuay furnace repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
CODE: SLOW AMBER FLASH
PROBLEM: Normal operation with call for heat
CODE: RAPID RED FLASH
PROBLEM: Twinning error, incorrect 24V phasing.
FIX: Check twinning wiring. Flame sense current is below 1.5 microamps
CODE: RAPID AMBER FLASH
PROBLEM: Check and clean flame sensor. Check for proper gas flow. Verify that current is greater than 1.5 microamps at flame current test pad.
CODE: 4 AMBER FLASHES
PROBLEM: The control is receiving a “Y” signal from the thermostat without a “G” signal, indicating improper thermostat wiring.
CODE: 1 RED FLASH
PROBLEM: This indicates that flame was sensed when there was not a call for heat.
FIX: The control will turn on both the inducer motor and supply air blower. A gas valve that leaks or is slow closing would typically cause this fault.
CODE: 2 RED FLASHES
PROBLEM: This indicates that the normally open pressure switch contacts are stuck in the closed position.
FIX: The control confirms these contacts are open at the beginning of each heat cycle. This would indicate a faulty pressure switch or miswiring. This indicates the normally open pressure switch contact did not close after the inducer was energized.
CODE: 3 RED FLASHES
PROBLEM: This could be caused by a number of problems: faulty inducer, blocked vent pipe broken pressure switch hose or faulty pressure switch.
CODE: 4 RED FLASHES
PROBLEM: This indicates that the main limit switch has opened its normally closed contacts.
FIX: The control will operate the supply air blower and inducer. This condition may be caused by: dirty filter, improperly sized duct system, incorrect blower speed setting, incorrect firing rate or faulty blower motor. Also, this fault code could be caused by a blown fuse located on the control board.
CODE: 5 RED FLASHES
PROBLEM: This fault is indicated if the normally closed contacts in the rollout switch opens.
FIX: The rollout control is manually reset. If it has opened, check for proper combustion air, proper inducer operation, and primary heat exchanger failure or burner problem. Be sure to reset the switch and cycle power (24 VAC) to the control after correcting the failure condition. Also, this fault code could be caused by a blown fuse located on the control board.
CODE: 6 RED FLASHES
PROBLEM: This indicates that after the unit was operating, the pressure switch opened 4 times during the call for heat.
FIX: If the main blower is in a “Delay on” mode, it will complete it, and any subsequent delay off period. The furnace will lock out for one hour and then restart.
CODE: 7 RED FLASHES
PROBLEM: This fault code indicates that the flame could not be established. This no-light condition occurred 3 times (2 retries) during the call for heat before locking out.
FIX: Low gas pressure, faulty gas valve, dirty or faulty flame sensor, faulty hot surface ignitor or burner problem may cause this. The furnace will lock out for one hour and then restart.
CODE: 8 RED FLASHES
PROBLEM: This fault is indicated if the flame is lost 5 times (4 recycles) during the heating cycle.
FIX: This could be caused by low gas pressure, dirty or faulty flame sensor or faulty gas valve. The furnace will lock out for one hour and then restart.
CODE: 9 RED FLASHES
PROBLEM: Indicates reversed line voltage polarity or grounding problem.
FIX: Both heating and cooling operations will be affected. check polarity at furnace and branch. Check furnace grounding. Check that flame probe is not shorted to chassis.
CODE: 10 RED FLASHES
PROBLEM: Flame sensed with no call for heat.
FIX: Check gas valve and gas valve wiring This indicates that a primary or auxiliary limit switch has opened its normally-closed contacts and has remained open for more than five minutes.
CODE: 11 RED FLASHES
PROBLEM: This condition is usually caused by a failed blower motor or blower wheel.
FIX: Cycle power (24 VAC) to the control to reset the hard lockout condition after correcting the failure condition.
CODE: 12 RED FLASHES
PROBLEM: This code indicates an open igniter circuit.
FIX: This could be a disconnected or loose wire or a cracked or broken igniter.
CODE: STEADY ON RED
PROBLEM: Control failure.
FIX: Replace control board.
CODE: 60-MINUTE AUTOMATIC RESET FROM LOCKOUT
PROBLEM: This control includes a “watchdog” type circuit that will reset from a lockout condition after 60 minutes. Operational faults 6, 7, 8 will be reset. This provides protection to an unoccupied structure if a temporary condition exists causing a furnace malfunction. An example would be a low incoming gas supply pressure preventing unit operation When the gas pressure is restored, at some point the “watchdog” would restart the unit and provide heat for the house.
CODE: IGNITION CONTROL FLAME SENSE LEVELS
PROBLEM: Normal flame sense current is approximately 3.7 microamps DC Low flame signal warning starts at 1.5 microamps. Low flame signal control lockout point is 0.1 microamps DC.
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneOctober 31, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedOctober 31, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesOctober 31, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceOctober 31, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesOctober 31, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierOctober 31, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeOctober 31, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.October 31, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobOctober 31, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingOctober 31, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.