If you’re looking for help fixing your Carrier furnace, look no further! Our comprehensive Carrier furnace repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
Rapid LED flashing – Line voltage polarity is reversed.
If twinned, refer to twinning kit instructions.
Error Code 1-1 – No previous code
Stored status codes are erased when power to control is interrupted.
Error Code 1-2 – The blower is on after power up
Blower runs for 90 seconds if the unit is powered up during a call for heat.
Error Code 1-3 – Limit or flame roll-out switch lockout
Control will auto-reset after 3 hours. Reset the switch or replace the fuse link.
Error Code 1-4 – Ignition lockout
Control will auto-reset after 3 hours.
Error Code 2-1 – Gas heating lockout
Control won’t auto-reset. Check for either a badly-wired gas valve or a defective control.
Error Code 2-2 – Abnormal flame-proving signal
Flame is proved while the gas valve is de-energized. Check for either a leaky or stuck-open gas valve.
Error Code 2-3 – Pressure switch didn’t open
Check for an obstruction in the pressure tubing or a pressure switch that is stuck closed.
Error Code 2-4 – Secondary voltage fuse is open
Check for a short circuit in the secondary voltage wiring.
Error Code 3-1 – Pressure, draft safeguard, aux-limit switch, or blocked vent switch didn’t close (or reopened, downflow only)
If open for longer than 5 minutes, the inducer will shut off for 15 minutes before retry. Check for: low inducer voltage; proper vent sizing; defective inducer motor; defective blower motor or capacitor; defective pressure switch; restricted vent; excessive wind, inadequate combustion air supply; or obstructed pressure tubing.
Error Code 3-3 – Limit or flame roll-out switch is open
If the switch is open for longer than 3 minutes, the code will change to #1-3. Flame roll-out switch requires manual reset. Check for: defective blower motor or capacitor; dirty filter or restricted duct system; loose blower wheel; faulty switch or connections; or inadequate combustion air supply.
Error Code 3-4 – Ignition proving failure
Control will try three more times before lockout #1-4 will occur. If the flame signal is lost after the trial for ignition period, the blower will come on for a 90 second recycle delay. Check for: build-up on the flame sensor; proper microamp distribution to the flame sensor; defective gas valve or turned off gas valve; faulty hot surface ignitor; low inlet gas pressure; the manual valve is shut-off; continuity of control ground; low flame carryover or rough ignition; ungrounded flame sensor.
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneJune 11, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedJune 11, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesJune 11, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceJune 11, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesJune 11, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierJune 11, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeJune 11, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.June 11, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobJune 11, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingJune 11, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.