If you’re looking for help fixing your Coleman furnace, look no further! Our comprehensive Coleman furnace repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
CODE: Slow amber flashing
PROBLEM: Normal operation with a call for heat.
CODE: Steady on red
PROBLEM: There’s a control failure.
CODE: Rapid red flashing
PROBLEM: There’s a twinning error with incorrect 24V phasing.
FIX: Check the twinning wiring.
CODE: Rapid amber flashing
PROBLEM: There’s a low flame sense current.
FIX: Check and clean the flame sensor. If it’s still an issue, check for proper gas flow.
CODE: One red flash
PROBLEM: A flame’s present with the gas turned off.
FIX: Check the gas valve. It could be leaky or slow closing.
CODE: Two red flashes
PROBLEM: Pressure switch is stuck in the closed position.
FIX: Check if there is a faulty pressure switch or miswiring.
CODE: Three red flashes
PROBLEM: Pressure switch is stuck in the open position.
FIX: Check if there is a faulty inducer, a blocked vent pipe, a broken pressure switch hose, or a faulty pressure switch.
CODE: Four red flashes
PROBLEM: Limit switch is stuck while open.
FIX: Check for a a dirty filter, an improperly sized duct system, an incorrect blower speed setting, or a faulty blower motor.
CODE: Five red flashes
PROBLEM: Rollout switch is stuck while open.
FIX: The rollout control is manually reset. Therefore, if it has opened, then check to see if the inducer is operating properly or there is an issue with the primary heat exchanger.
CODE: Six red flashes
PROBLEM: Pressure switch cycle has locked out.
FIX: The furnace will lockout for one hour and then reset.
CODE: Seven red flashes
PROBLEM: There’s an ignition lockout due to too many retries.
FIX: The flame couldn’t be established, check for a faulty gas valve, a dirty or defective flame sensor, a faulty hot surface ignitor, or a problem with the burner.
CODE: Eight red flashes
PROBLEM: There’s an ignition lockout due to repeated power recycles.
FIX: Check if there is low gas pressure, a dirty or defective flame sensor, or a faulty gas valve.
CODE: Nine red flashes
PROBLEM: There’s a grounding or line polarity issue.
FIX: Check the polarity at both the furnace and branch.
CODE: Ten red flashes
PROBLEM: Gas continues to flow with no call for heating.
FIX: Check on the gas valve and the gas valve wiring.
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneAugust 25, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedAugust 25, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesAugust 25, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceAugust 25, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesAugust 25, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierAugust 25, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeAugust 25, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.August 25, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobAugust 25, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingAugust 25, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.