If you’re looking for help fixing your ComfortMaker furnace, look no further! Our comprehensive ComfortMaker furnace repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
CODE: Two LED flashes
PROBLEM: Pressure switch stuck closed
FIX: Obstruction in pressure tubing
CODE: Three LED flashes
PROBLEM: Pressure switch stuck open or manual ON/OFF switch in off position
FIX: Proper vent size; defective inducer motor; excessive wind; faulty pressure switch; disconnected or obstructed pressure tubing; inadequate combustion air supply; or restricted vent
CODE: Four LED flashes
PROBLEM: The limit switch is open
FIX: Loose blower wheel; restricted vent; dirty air filter; defective blower; or excessive wind
CODE: Five LED flashes
PROBLEM: Flame has been sensed out of sequence
FIX: The gas valve is either leaking or stuck open
CODE: Six +1 LED flashes
PROBLEM: Soft lockout: maximum trials for ignition has been reached
CODE: Six +2 LED flashes
PROBLEM: Soft lockout: flame sense was lost while running, a cycling pressure switch, or blocked condensate
CODE: Six +3 LED flashes
PROBLEM: Soft lockout: the pressure switch was opened during run
CODE: Six +4 LED flashes
PROBLEM: Soft lockout: the limit switch was opened during run
CODE: Seven LED flashes
PROBLEM: Soft lockout: the main limit was open for too long (1-hour delay)
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneSeptember 27, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedSeptember 27, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesSeptember 27, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceSeptember 27, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesSeptember 27, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierSeptember 27, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeSeptember 27, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.September 27, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobSeptember 27, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingSeptember 27, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.