If you’re looking for help fixing your Goodman furnace, look no further! Our comprehensive Goodman furnace repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
CODE: Single LED flash, steadily on
PROBLEM: This means your Goodman furnace has no signal coming from the thermostat and won’t operate.
FIX: You should check your thermostat for an improper setting or connection.
CODE: Single LED flash, blinks on and off
PROBLEM: This means that your furnace has locked out due to too many ignition attempts.
FIX: After one hour of lockout, your furnace will automatically reset itself.
CODE: Two LED flashes
PROBLEM: This means that the draft blower isn’t functioning properly, or your furnace has a short in the pressure switch circuit.
FIX: You should either repair the short or replace the pressure switch.
CODE: Three LED flashes
PROBLEM: This means your furnace has an open pressure switch circuit or the induced draft blower is operating when it shouldn’t be.
FIX: You should check the pressure switch hose for blocks or an improper connection. Otherwise, see if any loose wiring needs tightening.
CODE: Four LED flashes
PROBLEM: This means your furnace has a primary open limit circuit.
FIX: You should check and clean all the filters, tighten the wiring, and see if there are any blockages in the flue.
CODE: Five LED flashes
PROBLEM: This means that your furnace senses a flame without a call for heat.
FIX: You should check for a leaky or open gas valve or a lingering burner flame.
CODE: Seven LED flashes
PROBLEM: This warns of a low flame sense microamp signal. This is the result of a coated flame sensor or a lazy flame due to poor gas pressure.
FIX: Adjust the gas pressure according to the information available to you.
CODE: Eight LED flashes
PROBLEM: This means your furnace has an igniter circuit problem due to a defective igniter or an improperly connected igniter.
FIX: Replace the igniter or check the ground wiring for defects.
CODE: Nine LED flashes
PROBLEM: This means that your furnace has a high-stage pressure switch that won’t close during a high-stage-induced draft blower operation.
FIX: Check your Goodman furnace for a pinched or blocked pressure switch hose.
CODE: Continuous LED flashes
PROBLEM: This means that your furnace has a reversed polarity of 115 volts.
FIX: You will have to correct the wiring polarity after reviewing the wiring diagram.
goodman furnace codes
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneAugust 7, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedAugust 7, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesAugust 7, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceAugust 7, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesAugust 7, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierAugust 7, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeAugust 7, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.August 7, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobAugust 7, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingAugust 7, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.