If you’re looking for help fixing your Rheem air conditioner, look no further! Our comprehensive Rheem air conditioner repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
CODE: Error Code C
PROBLEM: Unit is operating normally and in a cooling stage.
FIX: Normal operation.
CODE: Error Code Flashing C
PROBLEM: Cooling was commanded during an active anti-short cycle.
FIX: Wait until unit timer has expired or press the TEST button to defeat short cycle delay.
CODE: Error Code D1
PROBLEM: No shared data.
FIX: Replace memory card with correct system information.
CODE: Error Code D3
PROBLEM: Airflow mismatch.
FIX: Replace with properly sized air handler.
CODE: Error Code D4
PROBLEM: Memory card in control board is invalid.
FIX: Check if memory card is present and ensure it matches device.
CODE: Error Code D8
PROBLEM: Old shared data system data is obsolete.
FIX: If system will not operate, order new memory card to update system information.
CODE: Error Code T
PROBLEM: Unit is in test mode.
CODE: Error Code P
PROBLEM: There’s no current going to the compressor.
FIX: Check to see if the motor protector is open or line voltage is disconnected.
CODE: Error Code 1
PROBLEM: The compressor is running continuously.
FIX: Check to see if there is low refrigerant, air duct leakage, a dirty outdoor coil, or a dirty air filter.
CODE: Error Codes 02, 29, and flashing L29
PROBLEM: High-pressure problem.
FIX: Check if there is a dirty outdoor coil, outdoor fan is not running, liquid line restriction, or excessive refrigerant charge.
CODE: Error Code 03
PROBLEM: Unit is short-cycling.
FIX: Check thermostat wire connections (R. C. 1. & 2) and thermostat location in zone (too close to discharge grill).
CODE: Error Codes 05, 06, 07, L6, and L7
PROBLEM: Problem with the compressor because of an open circuit.
FIX: Check for damaged, miswired. or wrong run capacitor, broken wires, loose connectors, or miswired compressor, compressor windings for continuity, and open compressor internal protector.
CODE: Error Codes L4
PROBLEM: The rotor is locked.
FIX: Check if there is a bad run capacitor, low line voltage, excessive refrigerant in compressor, or seized bearings in compressor.
CODE: Error Code 09
PROBLEM: Secondary voltage is low.
FIX: Check if the control transformer is overloaded or for low line voltage.
CODE: Error Codes 21 and flashing L21
PROBLEM: Low-pressure control is open.
FIX: Check if unit has low refrigerant charge, indoor coil is frozen, dirty indoor coil or filter, indoor blower is not running, or expansion valve is not operating correctly.
CODE: Error Code 27
PROBLEM: Low or no line voltage.
FIX: Check incoming line voltage to the disconnect and unit and wiring connections.
CODE: Error Code 28
PROBLEM: High line voltage fault.
FIX: Check line voltage.
CODE: Error Code 30
PROBLEM: On-board fuse is open.
FIX: Check if low voltage wiring at R and C is damaged or miswired.
CODE: Error Code 80
PROBLEM: Unit isn’t meeting minimum airflow requirements.
FIX: Replace with properly sized unit.
CODE: Error Code 83
PROBLEM: Problem with the condenser coil temperature.
FIX: Check sensor is installed correctly on control and replace the sensor.
CODE: Error Code 84
PROBLEM: Problem with the outdoor ambient temperature fault.
FIX: Check unit placement. If the outdoor unit is in a high temperature area, wait until the ambient temperature drops and check sensor reading. Check sensor is installed correctly on control. Replace the sensor.
CODE: Error Code 93
PROBLEM: There’s a problem with the internal control.
FIX: Check control for proper system operation. Replace control.
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneAugust 8, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedAugust 8, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesAugust 8, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceAugust 8, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesAugust 8, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierAugust 8, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeAugust 8, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.August 8, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobAugust 8, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingAugust 8, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.