If you’re looking for help fixing your Tempstar air conditioner, look no further! Our comprehensive Tempstar air conditioner repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
PROBLEM: Normal operation – No call for cooling with 2-wire connection or indoor unit not pow-Offered.
CODE: 1 pause
PROBLEM: Normal operation.
PROBLEM: Communication with wall control lost. Check wiring to wall control, indoor and outdoor units.
PROBLEM: High pressure switch trip. Check refrigerant charge, outdoor fan operation and coils for airflow restrictions.
PROBLEM: Low pressure switch trip. Check refrigerant charge and indoor air flow.
PROBLEM: Outdoor unit control board has failed. Control board needs to be replaced.
PROBLEM: The control voltage is less than 15.5v for at least 4 seconds. Compressor and fan operation not allowed until control voltage is a minimum of 17.5v. Verify control volt-age.
PROBLEM: Outdoor air sensor not reading or out of range. Ohm out sensor and check wiring.
PROBLEM: Coil sensor not reading or out of range. Ohm out sensor and check wiring.
PROBLEM: Improper relationship between coil sensor and outdoor air sensor. Ohm out sensors and check wiring.
PROBLEM: Compressor voltage sensed after start-up, then absent for 10 consecutive seconds while cooling demand exists. Possible causes are internal compressor overload trip orloss of high voltage to compressor without loss of control voltage. The control will continue fan operation and wait 15 minutes to attempt a restart. Fault will clear when restart is successful, or low voltage power is cycled.
PROBLEM: Compressor voltage sensed when no demand for compressor operation exists. Contactor may be stuck closed or there is a wiring error.
PROBLEM: Compressor voltage not sensed when compressor should be starting. Disconnect may be open or contactor may be stuck open or there is a wiring error.
What Our Clients Are Saying About Us
I would like to recommend your company to anyoneOctober 10, 2020
Your company KDM Home & Gas has just installed the CV 50 water heater to my house. The installation process was so smooth. You guys put on the carpet runner in order to avoid any scratch and damage to the carpet and the floor. Your professional guidance has highlighted the B Vent should be installed for the chimney exhaust in order to comply with the building & safety code. You have even performed leak test & dial test in order to make sure the whole installation is in a perfect manner. The registration of the warranty is also very convenient and easy.
I really appreciated that you came to my house to inspect the situation and provide the quotation to me before we decide to get the new water heater. The whole process was so smooth and communicate very well. You return all my text message on the same day basis or even within short time. I would like to recommend your company to anyone.
Work was done neatly. Can barely see the pipe that was installedOctober 10, 2020
Work was done neatly. Can barely see the pipe that was installed. Priced really well.
KDM's cost was amazingly reasonable compared to all other quotesOctober 10, 2020
The tricky plumbing job was completed carefully and thoroughly . Daniel even did extra to make the job proper, within the quote . He patiently explained the work needed before and after completion . In good time, he returned calls and messages, detailed the work, listed every cost honestly, and answered any questions pleasantly . Daniel and his partner were always courteous, and respectful to keep the work clean in my house .
The replaced part is of high quality, thank you ! And his cost were amazingly reasonable compared to all other quotes.
I would recommend this company to anyone who is looking for a professional job at a reasonable priceOctober 10, 2020
KDM did a very professional job paying attention to safety and TSSA codes for this type of work.
At the end of the job they tested all gas fired appliances as they had the main gas off to preform this job, and made sure everything was working proper.
I would recommend this company to anyone who is looking for a professional job at a reasonable price.
I would recommend KDM Home Gas to anyone looking for quality home repair servicesOctober 10, 2020
Daniel was really great to work with. His communication and genuine care for the work being done made all the difference in the world to me especially as we’ve never had good experiences with contractors in the past.
Daniel showed up when he said he would, and took his time to explain to me what caused my humidifier to malfunction. His customer service skills are superior and his quality workmanship made the experience a pleasant one.
I would recommend KDM Home Gas to anyone looking for quality home repair services to their heating or cooling units.
Thank you guys! We couldn’t be happierOctober 10, 2020
Dan and his team were extremely professional, courteous, and clean. They showed up on time, and completed the installation exactly when they said they would finish by. Thank you guys ! We couldn’t be happier.
I highly recommend KDM HomeOctober 10, 2020
Daniel, Shane and Steve did a great job replacing our 3 appliances today. They’re true professionals that pride themselves on making sure everything is done correctly, within budget and on time. They answered all my questions and were more than willing to give helpful advice. I highly recommend KDM Home.
I would recommend KDM Home & Gas to anyone looking for great service at a good price.October 10, 2020
After our old (20+ years) unit gave out, I used HomeStars to obtain quotes for a replacement. Within 30 minutes of posting, I was speaking with Daniel, who was polite and helpful throughout the process. He offered a fair price and a few different products to choose from, and was able to do the installation the same week. I would recommend KDM Home & Gas to anyone looking for great service at a good price.
Great guys Daniel and Shane did an excellent jobOctober 10, 2020
Great guys Daniel and Shane did an excellent job clean efficient and on time also very knowledgeable will have them back to replace furnace.
KDM did our fireplace gas line and heat ventingOctober 10, 2020
We’re finishing our basement and had a gas line out in for a fireplace, as well as a heating vent out in bathroom.