If you’re looking for help fixing your Goodman air conditioner, look no further! Our comprehensive Goodman air conditioner repair guide will explain common issues, provide troubleshooting tips, and show you how to read your model’s error codes.
PROBLEM: Shorted sensor./Open sensor./Sensor disconnected./Sensor out of range.
PROBLEM: Short in low voltage wiring.
PROBLEM: Compressor relay contacts welded.
PROBLEM: Indoor blower motor problem./Communications error between indoor and outdoor unit.
PROBLEM: Indoor blower motor problem./Blocked filters./Restrictive/ undersized ductwork./Indoor-outdoor unit miss match
PROBLEM: Air conditioner/heat pump is wired as part of a communicating system and integrated control module does not contain any shared data.
PROBLEM: Air conditioner/heat pump is wired as part of a communicating system and integrated control module contains invalid shared data or network data is invalid for the integrated control module.
PROBLEM: Air conditioner/heat pump is wired as part of a communicating system and outdoor unit requires airflow greater than indoor unit’s airflow capability./ Shared data is incompatible with the system or missing parameters.
PROBLEM: Shared data sent to integrated control module does not match hardware configuration.
PROBLEM: Shared data on memory card has been rejected.
PROBLEM: Low refrigerant charge./Restriction in liquid line./Indoor blower motor failure. Indoor thermostat set extremely low.
PROBLEM: Blocked condenser coil./Outdoor fan not running.
PROBLEM: Intermittent thermostat demand./Faulty compressor relay.
PROBLEM: Compressor bearings are seized./Failed compressor run capacitor./Faulty run capacitor wiring./Faulty compressor wiring./Low line voltage.
PROBLEM: Power is disconnected./Failed compressor protector./Compressor not properly wired to control.
PROBLEM: Compressor start winding is open./Failed compressor run capacitor./Faulty run capacitor wiring./Compressor not properly wired to control./Faulty compressor wiring.
PROBLEM: Compressor run winding is open./Compressor no properly wired to control./Faulty compressor wiring.
PROBLEM: Low line voltage./ High line voltage.
PROBLEM: Control detects secondary voltage less than 18 VAC./Transformer overloaded./Low line voltage.
What Our Clients Are Saying About Us
I would recommend KDM for sureNovember 26, 2020
Dan was very friendly and polite from the start. Did exactly the work that we talked about on the phone, and was very quick making a late evening call on a Sunday. Tested all the joints and even painted the gas lines. I would recommend him for sure.
I would recommend KDM for any of the services they provideNovember 26, 2020
I had a 2nd hand pool heater hooked up and needed help getting it fired up. So I contacted Dan at KDM to see if they could help and was pleased he could make it over within a couple of days. He checked out the gas piping for leaks and proceeded to analyze the components of the control system and determined a faulty pressure switch was likely preventing operation. I was able to source the part and Dan was able to make a 2nd call within a day to install and complete the job. So in summary, I would recommend KDM for any of the services they provide.
KDM was hired for the Installation and relocation of internal gas lineNovember 26, 2020
KDM was hired for the Installation and relocation of internal gas line for my basement finishing project.
Daniel and Steve were amazing, very professional work and courteousNovember 26, 2020
Daniel and Steve were amazing, very professional work and courteous….never dealt with more friendly and knowledgeable Hvac technicians.
I would not hesitate to hire Daniel and his crew againNovember 26, 2020
Asked for quotes on a A/C and furnace after 17 years when the A/C unit broke down. I contacted a few HVAC contractors including KDM. Daniel could not have been more helpful and responsive and after reviewing the quotes decided to hire him for the job. Could no have made a better choice. Daniel was patient and upfront and answered all my questions when asked. He upgraded my A/C unit for the same price after the original unit we agreed upon was back ordered. The crew came when they said they would an completed the installation in a timely and orderly fashion.
I would not hesitate to hire Daniel and his crew again. In fact he is coming back to deal with another issue I have next month!
Job well done.
I definitely recommend KDM Home & gas for othersNovember 26, 2020
I was looking for someone who can do the gas line connection on a weekend and I found the right guys with KDM Home & Gas. Daniel came on Sunday morning to do the work. He installed the new gas line, connected the new gas stove, confirmed no leaks and ensured everything works fine. It was a really hot day outside but he did an excellent job.
Everything was quick and efficientNovember 26, 2020
Assessment happened on a holiday and work was completed the following day. Everything was quick and efficient.